Comentarios de la gente - Escribir un comentario
No encontramos ningún comentario en los lugares habituales.
Otras ediciones - Ver todas
added amount Balance Belmont Board bonds Carew Cast-Iron Cement-Lined cent Chapman Chapman Chapman Chapman Chapman Perkins Chapman Perkins Chapman charged Chestnut street City collected corner Chestnut corner Plainfield corner Water corner Worthington cost Court Cypress December Dwight street east from Main east side Eastern avenue end of pipe extension Federal feet fire Fisk flush fountains Franklin front gates H.-N. E. corner H.-N. W. corner Main Hampden Hancock High High High High Low Service Hill hydrants Inches interest James avenue laid Ludlow Main Ludlow reservoir MAIN AND DISTRIBUTION Main street Maple Matthews Meters midway Mill Myrtle N. W. corner North Main north side opposite park Perkins Chapman Chapman Pine Pleasant railroad receipts repairs School Service Service Service south side Spring Springfield Sumner supply Taylor terrace Union Walnut Wason west side Wilbraham road Willow Worthington street Wrought Iron
Página 30 - STATISTICS OF CONSUMPTION OF WATER. 1. Estimated total population at date 2. Estimated population on lines of pipe 3. Estimated population supplied 4. Total consumption for the year gallons. 5. Passed through meters gallons.
Página 27 - Dates of construction: — Original works in city, by private company, 1864 (Sale of same to city, for $238,296.00, in 1872.) Works at Ludlow, Mass., . . 1873-1874-1875 Works at Belchertown, Mass., . . . 1890-1891 Additional main from Ludlow reservoir, . 1893-1894 By whom owned, ..... City of Springfield Sources of supply: — Low pressure — from impounding reservoirs in the city fed by springs, surface water, and also by the high pressure. High pressure — from impounding reservoirs in Ludlow...
Página 12 - Total now in use miles. 6. Cost of repairs per mile $ 7. Number of leaks per mile 8. Length of pipes less than 4 inches diam miles.
Página 12 - Number of stop gates now in use, 541. 18. Number of stop gates smaller than 4-inch, 14. Number of blow-off gates, 15. Range of pressure on mains at centre of town, 65 Ibs.
Página 11 - ... outbreak, was called upon for his report. In this report, which was a preliminary one, Mr. Newlands stated that when he began his investigation the water supply was already under suspicion. Examination of this supply had shown it to be contaminated and a disinfecting plant was at once installed which resulted in a marked improvement in the quality of the water. The borough water supply is received from two reservoirs known as the Marshall Lake system and the HatchalusieCrystal Lake system, and...